CCMI utilizes testing equipment and methods which are widely accepted by local, state, federal, and regional regulatory agencies. In addition, CCMI maintains current certifications and licenses for testing, where applicable.
CCMI provides tank tightness testing through the use of the Estabrook EZY-3 Locator Plus tank tightness test method. This method is certified to test tanks up to 30,000 gallons in capacity and at product levels of 0-99% full.
CCMI uses the ACURITE test method for product line tightness testing. This test method is applicable to product line testing at gasoline service stations and bulk terminals. The ACURITE test method is capable of detecting leaks as low as 0.01 gallons per hour and can test pipelines with a maximum capacity of 150 gallons.
Mechanical and Electronic Line Detector testing is performed in accordance with the equipment manufacturer's requirements in order to verify the leak detector is capable of detecting a leak rate of 3.0 gallons per hour at 10 pounds per square inch.
Comprehensive Compliance Management, Inc. (CCMI) 31 West State Street - Unit B Granby, MA 01033 Phone/Fax: (413) 467-1124 email@example.com